Wuxi Fenigal Science & Technology Co., Ltd
Manufacturer and Supplier for Electrical & Lighting Products
|Place of Origin:||China|
|Minimum Order Quantity:||1 unit|
|Packaging Details:||Standard export carton|
|Delivery Time:||5-8 working days or bulk order negotiate|
|Payment Terms:||T/T, Western Union|
|Material:||Steel Case + Pure Copper Coil|
digital multifunction meter,
industrial control transformer
Chint Low Voltage TND/TNS(SVC) Single Phase Three Phase Automatic Voltage Stabilizer Power Supply Quality Component
TND1(SVC) Single-phase Automatic Voltage Regulator (0.5~30kVA)
TNS1(SVC) Three-phase Automatic Voltage Regulator (1.5~60kVA)
TND/TNS(SVC) series full-automatic AC voltage regulator collects sample and amplifies it and automatically control circuit, and drives the servomotor to rotate the rocker arm and brush in required direction, and finally adjusts the output voltage to the rated value, finally reaches the aim of stabilizing the voltage. It can be widely used in areas, where the mains voltage often comes across sharp fluctuation or sharp seasonal variation, such as industrial production, scientific research medical treatment & hygiene, household electrical appliances, it can provide any loads with excellent power supply.
Elegant appearance, compact structure, light weight, low power waste, complete protection functions, stable and reliable, low output waveform distortion and so on.
Ambient temperature: -15℃~+45℃.
Relative humidity ≤90%(at +25℃).
Working environment: Indoors, be free from chemical deposition, dirt, harmful corrosive medium, or flammable or explosive gas.
|Chint TND/TNS voltage stabilizer|
|Stabilizing time||<=3s with input volt fluactuating less than 20V|
|Harmonic distortion||No additional distortion|
protection set value
|246+/-4V phase voltage 246+/-4V|
protection set value
|180+/-4V phase voltage 180+/-8V|
The relation between output capacity and input voltage refer to as fig. 1 When input voltage less than 198V, the output capacity of product will decrease, the working capacity of stabilizer shall come down; when you choose output voltage of 110V, the out put capacity shall be not more than 50% rated capacity,to prevent overload.
The stabilizer is not allowed for working overloading long time, when the input phase voltage fluctuate within 198V ~ 250V (line voltage from 342V ~ 430V), at emergent case, it is allowed to work as specified
Contact Person: harry