Wuxi Fenigal Science & Technology Co., Ltd
Manufacturer and Supplier for Electrical & Lighting Products
|Place of Origin:||China|
|Model Number:||Star-delta starter / Custom|
|Minimum Order Quantity:||1 Unit|
|Packaging Details:||Standard export carton/crate wood box|
|Delivery Time:||5-8 working days or bulk order negotiate|
|Payment Terms:||T/T, Western Union|
|Material:||Galvanized Sheet Steel / JXF Enclosure||Color:||White,gray,RAL 7035|
|Application:||To Start AC 3 Phass Squirrel Cage Motor Safely||Type:||Motor Control, Power Distribution System|
|Protection Level:||IP54||Rated Voltage:||220/380V,120V/240V|
|Function:||Reduced Voltage Start And Protection Of AC Motor||Certification:||CE|
|Working Temperature:||-40 To +80 Degrees Centigrade||Name:||Star-delta Starter/Distribution Cabinet/Power Electric Meter Box|
|Mounting Type:||Flush Or Surface|
distribution board box,
industrial power distribution board
Star-delta Starter Motor Control Board for 15~45kW Water Pump or Fan Start at Reduced Voltage 380V~415V 3 Phase
Most induction motors are started directly on line, but when very large motors are started that way, they cause a disturbance of voltage on the supply lines due to large starting current surges.
To limit the starting current surge, large induction motors are started at reduced voltage and then have full supply voltage reconnected when they run up to near rotated speed.
Working Principle of Star-Delta Starter
This is the reduced voltage starting method. Voltage reduction during star-delta starting is achieved by physically reconfiguring the motor windings as illustrated in the figure below. During starting the motor windings are connected in star configuration and this reduces the voltage across each winding 3. This also reduces the torque by a factor of three.
Scheme – Working Principle of Star-Delta Starter
After a period of time the winding are reconfigured as delta and the motor runs normally. Star/Delta starters are probably the most common reduced voltage starters. They are used in an attempt to reduce the start current applied to the motor during start as a means of reducing the disturbances and interference on the electrical supply.
The Star/Delta starter is manufactured from three contactors, a timer and a thermal overload. The contactors are smaller than the single contactor used in a Direct on Line starter as they are controlling winding currents only. The currents through the winding are 1/root 3 (58%) of the current in the line.
There are two contactors that are close during run, often referred to as the main contractor and the delta contactor. These are AC3 rated at 58% of the current rating of the motor. The third contactor is the star contactor and that only carries star current while the motor is connected in star.
The current in star is one third of the current in delta, so this contactor can be AC3 rated at one third (33%) of the motor rating.
We provide star-delta starter control board integrating Chint l low-voltage components below, with normal range from 15kW, 18.5kW, 22kW, 30kW, 37kW to 45kW at rate voltage AC380V/50Hz.
15kW Star-delta Starter
18.5kW Star-delta Starter
22kW Star-delta Starter
30kW Star-delta Starter
37kW Star-delta Starter
45kW Star-delta Starter
Contact Person: Mr. Harry